EBI’s scope included IPB inspection, cleaning, and repairs to the generator cabinet. Once onsite, EBI disassembled neutral box and GTE box bars and braids. EBI sanded and silver plated all mating surfaces. EBI supplied and installed new braided flex links from CT plates to IPB bars. EBI reinstalled all neutral box and GTE box components with new hardware, torqued and DLRO’d. EBI cleaned neutral box and GTE box and insulators. EBI installed all access doors with new gasket material and hardware. EBI then cleaned all work areas and demobilized site.